IP56 Marine frequency converter (380V or 400V or 10KV) 40KVA-350KVA
Marine frequency converter(380V or 400V or 10KV ) are specially used in ports, dockyard fitting-out berth, shipbuilding,shiprepairing and oil drilling platforms,which is made by world-class technology of ours.
Marine frequency converters are specially used in ports, dockyard fitting-out berth, ships and ocean drilling platforms with outdoor harsh environments which need outdoor frequency conversion variables with high reliability of power supply. This series of products adopt full sealed three layers of insulation pipeline with full air conditioning circulation protection. Inside of equipment environment is completely isolation with the outside world. Equipment tank protection level IP56, fully meet the shore wharf, ships and drilling platforms with any harsh outdoor environments. A complete set of equipment in accordance with the standard container box shape design, easy to transport and move often.
●Using the full sealed air conditioning cooling system with three insulation layer tank to ensure that the equipment is under good protection.
●Adopting the latest instantaneous voltage waveform control technology, output voltage fluctuation≤0.5V,when 100% load, the output voltage fluctuation less than 3% and recover to the rated output voltage value in 0.5 wave cycle.
●Adopting technology of pure sine inverter output filter. Reduce the output impedance of the sinusoidal filter and improve the quality of the output power.
●Driven by our module with signal master-slave synchronization parallel technology. Which can realize parallel working of many shore variable power equipments without current circulation interference.
●Using the power switching devices which is made by Germany, DSP core is made by USA with 5Mhz optical fiber driver transmission mode. The inverter modulation method adopts the latest SVPWM space vector pulse width modulation.
|Input Voltage||380/400VAC±10%/10KV±10%,3phases,can be customized special voltage input according to customersrequirements|
|Rectifier||6pluses or PWM|
|Power factor||6pluses>0.95; PWM>0.99|
|THDi||<35%(6pluses at 100%load)or<5% (PWM at 100% load)|
|Output Voltage||440VAC, 6.6KV (can be customized special voltage output)|
|Voltage Stabilizing||<0.5V at static; <±1%(dynamic,0-100%load)|
|Frequency||50Hz or 60Hz (precision:0.01)|
|Overload ability||125% for 1minute; 150% stop output;can withstand 3 times of instant impact|
|Total harmonic distortion of output voltage THDu||≤1％(no load or line load )|
|Peak coefficient of output voltage CF||1.4+0.1(No load)|
|Three phase output voltage imbalance||<1%|
|Phase angle of three-phase output voltage||120°（±0.1°）|
|Inverter main circuit topology||Germany SKIIP fourth-generation half-bridge IPM intelligent power module constitutes a three-phase full-bridge inverter circuit|
|Inverter adjustment method||SVPWM space vector pulse width modulation method|
|Voltage stabilizing control||Instantaneous voltage waveform feedback control method|
|Inverter switch frequency||3.6KHZ～6KHZ|
|PWM Drive Transmission Mode||5MHZ fiber drive transmission|
|Sinusoidal filtering method||Three-stage sinusoidal filter at output of inverter|
|Display||LCD display or touch screen display|
|Input display||Display input power three-phase line(phase) voltage, frequency, three-phase line current, input voltage harmonic analysis, visual power, active power, reactive power, power factor, active power meter, reactive power measurement. (Display and measurement accuracy is 0.5)|
|Output display||Display output power three-phase line(phase) voltage, frequency, three-phase line current, output voltage harmonic analysis, visible power, active power, reactive power, power factor, active power measurement, reactive power measurement. (display and measurement accuracy 0.5)|
|System Parameters Display||System operation time, DC bus voltage, power module output current, inverter switch frequency, output voltage setting value, output frequency setting value, input Transformer temperature, rectifier|
Temperature, three-phase power module temperature, sinusoidal filter temperature, output Transformer temperature.
|Fault display||Show fault alert information graphically and permanently record all running data when a failure occurs for future analysis of the failure|
|Operation display||Display information such as system state, operation prompt, fault location and handling method to facilitate operators operation and maintenance of equipment|
|Drawings Data Display||Each set of variable frequency power supply is permanently stored the drawings, instructions and other technical data of the variable frequency power supply, and it is very convenient to consult|
|Compressive strength||Low pressure: 2500V/AC, 1 minute, no breakdown fire phenomenon(leakage current 10mA); High Pressure: 42 KV/AC, 1 minute, should not break through the fire phenomenon|
|Cold insulation resistance||≥100MΩ|
|Environment||Ambient temperature is -5 °C to +45 °C, and the relative humidity is 0 to 95 °C,Working for 24 hours at 100% full load,the temperature in the equipment cabin is in the range of 25 °C ± 1 °C|
|Protection Class||IP66 for equipment, fully sealed insulation; IP56 for Air conditioning|
|Protection||Input power supply phase sequence, phase deficit(three-phase imbalance), undervoltage, overvoltage, overcurrent, short circuit, DC bus overvoltage (protection threshold can be set )|
|The output power supply produces phase deficiency, undervoltage, overvoltage, Overflow, short circuit, output voltage harmonic overvalue, (protection threshold can be set )|
|Transformer temperature, sinusoidal filter temperature, rectifier temperature, IPM power module exceeds normal operating temperature, frequency converter power supply trips protection. (Temperature value can be set)|
|When the transformer temperature and the sinusoidal filter temperature reach the fan starting temperature, the corresponding fan is started for forced wind cooling. (Temperature value can be set)|
|Considering the control of different power loads, when the output load capacity reaches any setted value, the sound and light pre-alarm signal is issued.After the overload alarm signal is issued for 1 minute, variable frequency power supply stops to be protection(the setting can be adjustable)|